Lifting check valve structure:
Lifting check valve is a kind of valve that prevents pipeline media from flowing back, mainly composed of valve body, valve seat, valve flap, valve cover and other related parts. The lift check valve is equipped with a spring to ensure that the disc is always in a dynamic equilibrium state under the action of the spring. Regardless of the medium pressure at the inlet of the valve, the valve can maintain a balanced operation.
The working principle of the lift check valve:
The lift check valve has a guide rod on the disc, which can move up and down freely in the guide hole of the valve cover. When the pipeline medium flows in in the specified direction (from left to right), and the pressure below the valve flap exceeds the pressure above it, push the valve flap to rise along the center line of the guide hole of the valve cover, and the valve will automatically open to allow the medium to flow; if the fluid flows from the right to the right Left flow, that is, when it flows backward, the pressure above the valve flap is greater than the pressure below it. The pressure difference between the upper and lower pressures and the weight of the valve flap press the valve flap on the valve seat, so that the medium cannot pass through, that is, the fluid cannot flow back; and pipeline fluid The greater the pressure, the tighter the sealing surface is, and the better the sealing effect.
The seat sealing surface of the lift check valve can be welded, or it can be made into a seat sealing ring and then expanded or threaded on the valve body; when the valve body is made of stainless steel, the sealing surface can also be on the valve body It is directly processed from above. The sealing surface of the disc can be directly processed on the disc, or can be processed after surfacing or welded on the disc with the inner and outer periphery of the sealing ring. The straight-through lift check valve can only be installed on the pipeline in a balanced way, and the center line of the valve flap is vertical to the horizontal plane, while the vertical lift check valve is not subject to this restriction.