1. For static equipment
The vertical deviation of vertical equipment should not be greater than L/1000 and not greater than 10mm. Unless the drawings have special requirements.
The horizontal deviation of horizontal equipment should not be greater than L/1000 in the axial direction and 2D/1000 in the radial direction.
2. For moving equipment
When the pump is aligned, the selection of the installation datum and the allowable deviation of the level must meet the requirements of the “special specification” or the pump technical file. Generally, the allowable deviation of horizontal horizontality is 0.10mm/m, and the allowable deviation of vertical horizontality of the installation datum part is 0.05mm/m. The leveling and alignment values must not be adjusted by loosening the anchor bolts.
1. The pump that is disassembled and installed is based on the processing surface of the pump body, and the allowable deviation of the horizontality of the pump in the vertical and horizontal directions is 0.05mm/m.
2. The integrally installed pump should be leveled based on the inlet and outlet flange surface or other horizontal processing datum plane. The allowable deviation of horizontality is 0.05mm/m in the longitudinal direction and 0.10mm/m in the transverse direction.
3. When the driving shaft and the driven shaft are connected by a coupling, the centering deviation of the two shafts and the gap between the end faces of the two shafts should be:
Centering deviation: the radial displacement is not more than 0.03mm.
The axial tilt should not be greater than 0.05/1000.
The end face gap is 1.00~3.5mm.